How to Connect a Three-Phase Monitor Relay
Tuesday: August 4, 2015 : Three-Phase Monitor Relays
I have never connected a three-phase monitor relay. Do you have a typical wiring connection?
While each individual application may have its own requirements, this diagram showing a three-phase monitor relay and motor starter is fairly typical of most installations. When the three-phase voltage is present and all conditions are normal, the N.O. contact on the phase monitor relay (typically pins 1-8 on a plug-in product) closes, allowing the motor starter or contactor to be operated as normal. If a fault occurs, the phase monitor relay detects it and will open the N.O. contact, thus de-energizing the motor starter or contactor. When the fault goes away, the phase monitor relay will reclose its N.O. contact, but the motor starter or contactor will not energize until either a START pushbutton is closed or a two-wire control unit (i.e., limit switch, proximity switch, relay contact, etc.) is closed.
With the relay connected before the motor starter as shown above, the motor can be started in the reverse direction. However, the motor is unprotected against phase failures between the relay and the motor.
With the relay connected directly to the motor as shown below, the total feed lines are monitored. This connection should not be used with reversing motors, however.
Click here for more information on fusing these units.
Recent Articles for:
Three-Phase Monitor Relays
- Aug2019 Three-Phase Monitor Relays: What Motor Do You Need to Protect?
- Jul2019 Does my Phase Monitor Relay require a Short Circuit Current Rating?
- Jun2019 What type of power systems can Macromatic relays protect?
- Nov2018 Replacing a Square D (Schneider) 8430MPS or 8430MPD Phase Monitor Relay
- Jan2017 Isolated Alarm Circuit Output on Plug-in 3-Phase Monitor Relays